The selection of cable transport systems depends on various factors:
1. Cable Type:
Power cords are heated under load. Enough ventilation is required to dissipate heat. Cable ladders are the best choice in this regard. If it is a control and lighting cable, continuous support will be appropriate. In this case, the use of perforated or perforated cable ducts is necessary.
2. Cable Weight:
The total weight of the cables for the load capacity (kg / m) is an important factor. Cable ducts and cable ladders can be manufactured with different edge heights and different sheet thicknesses. Generally 100 mm. The load capacity for width is 15 kg / m. That's 600 mm. A cable ladder width of 90 kg / m. Cable load can be applied. (Depending on support distance)
3. Support Range:
Standard cable channels and stairs are 1.5 m. They are designed according to the support interval.
4. Mounting Direction: (horizontal or vertical)
The cables can be carried not only horizontally, but also vertically. For this purpose, the use of cable ladders is appropriate.
Galvanized surfaces as standard provide excellent protection against corrosion. Different coatings can be applied on standard galvanized to increase the resistance against corrosion. Ex: epoxy system electrostatic powder paint.